|Subdivision: STONE CROSSING AT MIDDLE CREEK||Filing: 3A||Subdivision Number: 6989|
|Address:12274 WOODMONT DR|
|Required Landscape:||Fire Codes:FUELS/A-ROOF|
Date In Date Out Status Reviewer Contractor Comments Rem 04/09/2021 4/14/2021 3:05:00 PM A KLS CREEKSIDE CUSTOM DECKS approval of 401 sf uncovered deck; meets setbacks and lot coverage does not exceed 35% if deck is 8' in height. no grading or vegetation removal permitted per disclaimer Add 01/02/2008 1/3/2008 D LAW ACUFF HOMES A retaining wall was constructed at the rear of the house that does not match the approved hillside site plan. This retaining wall that was constructed on site is not an approvable wall per City code. We do not allow retaining walls for the purpose of creating a flat yard in the hillside overlay. The approved hillside site plan also shows existing scrub oak that was to be saved (located outside the limit of disturbance). This scrub oak was removed and fill was brought in to create the flat yard that currently exists on site. To mitigate these issues the wall that was constructed on site will need to be removed and relocated to within 15’ of the house. Also re-vegetation will be required due to the unapproved removal of the scrub oak on site. 9 shrubs and 1 tree will be required to be planted on site. The additional retaining walls shown at the front and sides of the house are acceptable. This amount of retaining wall at the front and side is standard for this neighborhood. Note: The hillside certification statement is a note to be placed and signed on the site plan page. This is a new procedure our office has implemented, so please note this change for future hillside site plan submittals. New 12/26/2007 12/31/2007 D LAW Holding to review with BUV. New 05/03/2007 5/8/2007 A JMJ ACUFF HOMES TO BIN New 04/26/2007 4/30/2007 D JMJ ACUFF HOMES 1. Is there a sidewalk on this street? 2. Your topo line shows the 62 as the top of wall - will it be 62 or 64? 3. Limit of disturbance will be at least 10' from the house - show this on your plan. 4. Show the retaining wall on your real building elevation. 5. Show grade lines (proposed) in front as the site will be greated - your numbers have 72 at the garage corners but grade lines as shown don't indicate this.
For further information, please contact the Development Review Office @ 385-5982.